Sep. 03, 2021
The control panel is an important part of diesel generator set. It is generally divided into the automatic generator set control panel and the ordinary generator set control panel. At present, the top power generator manufacturers use the automatic generator set control panel, which can automatically complete the diesel generator control panel. Control functions such as starting and stopping, power supply and power failure of the generator set, and test, display, over-limit alarm and protection of the running state of the set. In this article, Dingbo Power will share with you the reasons and solutions for the failure of the control panel.
1. The diesel generator set alarms and shuts down, causing the control panel to malfunction. The control panel detects the failure of the diesel generator set and shuts down. At this time, the failure should be eliminated, and the power should be cut off (reset) and then restarted.
2. The mains power is normal and the unit cannot be stopped, causing the control panel to malfunction. Cause analysis and troubleshooting methods:
1) Re-cooling operation of diesel generator set (3~5 minutes).
2) ATS provides "start" signal and is not turned off, check ATS failure.
3) The oil machine instrument set the oil circuit solenoid valve of the unit incorrectly, and correct it in time.
3. When the mains fails and the diesel generator does not start, causing the control panel to fail, the general reasons are as follows:
1) The ATS control system fails to provide an "on" signal, check and troubleshoot.
2) The instrument of the self-starting oil machine is faulty, and it must be powered on and work in the "automatic" state.
3) The connection method of the control contact line is wrong, check and correct the connection method.
4) The instrument of the self-starting oil machine is faulty, repair or replace it.
4. The remote monitoring cannot be realized, resulting in malfunction of the control panel of the diesel generator set. Cause analysis and troubleshooting methods:
1) Confirm whether the unit is configured in accordance with "three remotes".
2) Confirm whether the communication line connection is correct.
3) Confirm whether the unit communication software is correctly installed on the control network computer.
4) Whether the communication is set according to the correct monitoring password.
The above are the common failure causes and solutions for the control panel of diesel generator set. The control panel is an indispensable part of the diesel generator set. Generally, the generator manufacturer will give it to the user when purchasing the diesel generator set. For reasonable matching, currently Dingbo Power, in addition to the supporting control screen, is also equipped with a Dingbo Power Cloud system that can realize remote monitoring. Users can realize remote data monitoring and alarm analysis of the unit through telephone and mobile phone, which greatly improves the management of the unit Efficiency.
Guangxi Dingbo Power Equipment Manufacturing Co., Ltd., as an authorized OEM partner of Volvo, can provide customers with high-quality, low fuel consumption, advanced performance, stable operation, safe and reliable various types of generator sets and comprehensive global warranty after-sales service. If you are interested to know more about our company and products, please contact us at firstname.lastname@example.org or call us by +86 13667705899 for details.
Jun. 24, 2022
Get in Touch